Originally Posted by HauteShots
I also took this video of the pilot flame:Pilot Flame Video
Does the flame look good?
I did not see your video, I don't know what program i would to find to open it.
If i was at your home checking this system out. First i would lit the pilot and see if is was blue and surrounding the power pile about 1/2" down from the top of the power pile and about 1/2" around the power pile. If it wasn't doing this then i would clean the pilot.
After the pilot is cleaned properly then i would take off the two power pile
wires from the gas valve, take my tester,lite pilot a and test the power pile to see if it is good or needs replacing. If the power pile tests ok and i put the wires back on the gas valve and the pilot still won't keep going, then the problem is in the magnet in the gas valve. later paul