amp probe the condensor fan motor circuit and the compressor circuit. compare this to the nameplate on each component and this will tell you which is tripping you out. this could be a bad capacitor. If the cap isn't doing it's job, the motor will overamp during startup. repeated stress on the fuse/breaker will eventualy trip/blow the fuse/breaker.