Gas Furnace, Electronic Ignition, Dust
My girlfriend has a two year old gas fired forced hot water system vented to the outside. We recently completed masonry repairs and generated a great deal of dust in the basement.
The heating system does not work properly, now. Her plumber came this AM and said the whole boiler needs to be taken apart and cleaned. I say only the parts which apply to the gas and heating side; the water and pumps are OK.
From memory it's a Weil-McLain, a small unit; it's a saltbox. What would be the expected costs for this operation?
Then they will have to Brush through the flue ways, and vacuum it out.
After all parts are cleaned , put it all back together. This would be a standard boiler. Service man would probably take about 4 to 5 hr.
So from there you would have to see what they would charge.
I would do this job for about $150.00plus gas for my truck, but some service men think they are worth $300.00 a hr. ????? Paul
Thanks, Paul. It turns out that apparently the cement dust was only part of the problem. BTW, you were correct about the time required.
The service man also said that there is not enough air in the small cellar for the burner to work efficiently and suggested a fan-fed intake from the exterior. The gas pressure was also low.
|All times are GMT -6. The time now is 09:01 AM.|