Gas furnace weak flame
I have Trane Gas furnace XE 60 at home and is producing a weak flame. I turned on the pilot and the flame comes but it is very weak. My house is cold ...please, please help. Somebody suggested that I adjust the screw on the pilot valve body but I don't 'see' it.
In coming pressure to low, Water in gas piping, water or dirt inside of gas valve,
The grease in the old gas cock plugging off the flow of gas, out side regulator
not passing the right gas pressure. It would be hard for you to try to adjust
the gas pressure on the gas valve with out having a pressure tester so you can get it right. You really need a tech to check this unit out. You would be testing
1/4 to1/2 lb of pressure so you should have a U tube to do this. later paul
|All times are GMT -6. The time now is 04:22 PM.|