||11-27-2011 06:13 PM
Trane XE90 Board
Originally Posted by NathanHale
hello everyone,i am new to this forum. i have a trane xe90 gas furnace. i just changed the board on it. my question is the old board had two terminals marked "PARK". i want to know into which terminal on the new board do the wires go into, in the new board?i see two of them say park on the new one and i am confused as to which wire from the old board goes where.thank you
Not sure what you are asking, but here is the answer i think you are looking for.
Your blower has 4 speeds, you put the speed you want for heating on the heat post. You put the speed you want on cooling on the cool post. The last two unused wires speeds go on the two parks. So is you want the same speeds you
had before then put the same two colored wires on the two parks and the same colors wired you had before on cool and heat.
Does this answer your question? The parks are just unused motor leads.