Originally Posted by BSB74
Thanks for posts guys. Yes nealtw, the switches will be in the same box together, but separately control each light independently. So I can run 14/3 cable from Light Fixture B (where power source enters) back to light switch box. Would the cable running from Light Switch A to Light Fixture A have to be 14/3 also or just 14/2 cable? Then basicly just wire up the light switches in the box and I should be good. Sorry for being such a newbie with this stuff and again thanks for the advise guys.
nealtw is right you only need 14-2 from A to A. Assuming your diagram is accurate.
Pretty basic. You run your 120V hot and neutral to light B, light A, and your plugs. Then you drop your 2 @ 14-2 switch legs from light A and B to your switches A and B.
But you should probably hire an electrician to check your work because a small mistake can lead to a big problem with this stuff.