Last Activity:01-13-2014 4:19 PM
Posted in thread: Unit quit working on 01-07-2014 at 10:08 AM
Good point Wasset! I have some of the basic voltages traciking this issue but did no take the
time to log as many as I should.
Posted in thread: Unit quit working on 01-06-2014 at 05:37 PM
Gentlemen, it was the Blower, Combustion motor. Working like a champ. The fan blades of the old
motor moved but grudgingly. But with power on did not turn at all.Thanks for the help and keep
Posted in thread: Unit quit working on 01-05-2014 at 05:09 PM
Wuzzat, thanks for the reply.The pressure switch is new as of this summer. I feel that is not
the problem. I leaning toward the fan motor due to the end being hot and it is not operating. I
Posted in thread: Unit quit working on 01-05-2014 at 02:23 PM
Trane XL 1200 - Model YCY030F1MOA not working. Main board is flasing indicating Pressure Switch
not working. If I close the contact on the Compressor Contactor Coil it turns on. When the back
of the b...