- Posts 9
Last Activity:10-21-2010 9:21 AM
Posted in thread: What BTU need to heating up 3000sf house on 04-10-2012 at 08:06 PM
This is a situation that you need a professional evaluation - you need what the business
referrs to as a Manual J heat gain-loss calculation. The furnace deals with the heating (heat
loss) side, while...
Posted in thread: Goodman Indoor Unit Rusty Coils on 04-10-2012 at 07:49 PM
If the coil gets blocked up every summer you might want to try a 4 to 1 mixture of lemon
flovored clorox and water into the drain pan each summer. This will kill any residual mold in
the pan and lines...
Posted in thread: A/C freezing up on 10-21-2010 at 09:21 AM
You need to find out why the filters were wet in the first place. There is no reason for
moisture getting into the return ductwork.There must be some air leakage in the return side for
water to get in...
Posted in thread: HVAC - Coil Cleaning on 10-20-2010 at 07:29 PM
Slove the problem first!Where is the dust comming from in the first place?A proper HVAC system
is a closed system - air is pulled across the filter where it is cleaned, goes to the unit
where it is he...
Posted in thread: HVAC design flaw? on 10-20-2010 at 07:02 PM
An excellent rule of thumb for return sizing is filter length x filter width x 2 = capacity, so
20 x 25 x 2 = 1000 cfm and 18 x 18 x 2 = 648. You have a nominal capacity of 1648 cfm and a 5
ton unit n...
Posted in thread: A/C freezing up on 10-20-2010 at 06:44 PM
Just because you charged and old unit in spring does not mean it is still charged properly.Does
the air velocity still feel the same?
Posted in thread: Insulation in cold air return? on 10-20-2010 at 06:33 PM
if this is loose insulation in an unlined return, the return suction pressure has pulled the
insulation in from the attic or walls. This means that your return trunk is not airtight and
Posted in thread: Re-routing furnace ducts in a old mobile home? on 10-20-2010 at 06:22 PM
Assume that you have a 2 1/2 ton air handler that moves 1000 cfm of air.Now assume that you are
loosing 20% (200 cfm) of this air under the house thru duct leakage. 1000 cfm is being sucked
Posted in thread: oil hot water problem on 10-20-2010 at 05:58 PM
1) if oil filter gasket is not 100% tight air can get into the line and shut it down2) same for
all oil piping connections3) cad cell could be getting weak4) dirty/blocked oil filter