Last Activity:02-16-2012 12:56 PM
Posted in thread: Heat pump fuse on 01-07-2010 at 12:24 PM
Charleston, WV maybe but not here. Slight chance of flurries but mostly just cold! Thanks for
the advice. I'll make sure it doesn't happen to that wire again.
Posted in thread: Heat pump fuse on 01-07-2010 at 11:48 AM
Thanks Maverick. Turned out to be one of the wires going to the reversing valve at the
compressor. It had laid up against the copper tubing and melted so that when the unit went into
"defrost mode" (i...
Posted in thread: Heat pump fuse on 01-05-2010 at 08:38 AM
Came home Sunday and heat wasn't working. Checked all breakers and disconnects. All good so I
opened the unit in the attic and found a 5 amp fuse blown. Replaced fuse and unit ran for about
1.5 hrs th...