Last Activity:12-04-2006 7:11 AM
Posted in thread: Dimmer Switch - 3 Way....No Way on 12-03-2006 at 07:19 AM
Ok, so I did not notice how my old dimmer was installed so have no idea what wires get
conencted where ?, The olde dimmer had yellow, red. black and green wires. Please helpI have a
- Possible mold problems??
- Installing new garbage disposal
- Need opinions on what to do here... (Pics Included)
- One Word Game
- Kitchen Faucet
- Funny Pictures and stories....
- Shower pan
- Need some help
- Lawnmower Question
- Musky smelling rugs
- Install Quarter Round when there is large gap underneath the baseboard?
- Water damage from a ceiling leak
- Window air condition unit
- Carrier AC Outside Fan Will Not Turn ON
- No Water Running Into or Out of Toilet
- Need some advice