- Posts 6
Last Activity:12-17-2008 4:47 PM
Posted in thread: unequeal heat pump/air handler tonnage on 06-19-2008 at 10:32 AM
an over sized condenser to a undersized evap coil can cause slugging this happens when the
liquid sent to the evaporator can not be completely evporated due to the smaller coil and lower
fan speeds th...
Posted in thread: One thermostat, two heat sources on 06-19-2008 at 09:56 AM
listen and please forgive the spelling you need a honeywell pro6000 with a 2 heat option pick
your primary heat source and wire that to w and secondary to aux or l . you can not mix the
input signal s...
Posted in thread: Freezing pipes on a heat pump on 06-19-2008 at 09:27 AM
if the filter is clean what you can do is get the model and serial of the furnace and find out
how many cfm's of air it can move and compare this to the ton's of the ac system you need 400
cfm per ton...
Posted in thread: Gas Line Tests - HELP! on 06-14-2008 at 08:15 PM
what he should do is get him to put at least 30 psi of nitogen which wont condense and spray
soap bubbles on every joint in the system I have seen the tracpipe adapters leak if the cut
wasnt clean if ...
Posted in thread: is this a good price for heatpump on 06-14-2008 at 07:56 PM
I wouldnt take my tools out of the truck for that hope you trust the guy scratch and dent means
no manufactuer warranteand a company has a reputation to protect and will repair mistakes for
at least a...
Posted in thread: Bad honeywell valve? on 06-14-2008 at 07:26 PM
this can be one that will leave a pro scratching his head connected to the inducer fan moter
and sometime a second hose to the heat exchanger will be some rubber hoses hooked to barb