- Posts 82
Last Activity:01-21-2016 5:02 PM
Likes Given: 4
50 Likes on 33 Posts
Posted in thread: Weather Head to Socket Meter SER/SEU Cable Upgrade on 01-21-2016 at 11:00 AM
hornetd: As far as house surge protection goes I was considering the Levington, but I heard
that the eaton MICRO and ULTRA are also good options. The levington would take too much room
(which means I ...
Posted in thread: Weather Head to Socket Meter SER/SEU Cable Upgrade on 01-21-2016 at 10:51 AM
hornetd: Sorry the delay in my follow up with this thread. I tried to use ¾ pvc conduit but it
was really difficult sleeve the wires inside the conduit, and I tried to use soap for no avail.
So I ende...
Posted in thread: Weather Head to Socket Meter SER/SEU Cable Upgrade on 01-11-2016 at 11:29 AM
That box is one way to bring the feeder conductors into the building but You may want to look
at a conduit fitting called an "LB" instead. LB means an L fitting with it's removable cover on
the back. ...
Posted in thread: Weather Head to Socket Meter SER/SEU Cable Upgrade on 01-04-2016 at 07:43 AM
Good to know no normal inspector would create any issue with what seems a non-issue matter. I
also plan on digging a small trench (maybe 4 inches deep) in order to have the bare copper #4
Posted in thread: to "derate" or not on 12-17-2015 at 10:56 AM
The copper industry would have you doing now. It is very common in USA to wire everything with
#12. Not so common in Canada.Wiring most residential structures entirely with #12AWG Copper is
a waste of...
Posted in thread: Weather Head to Socket Meter SER/SEU Cable Upgrade on 12-17-2015 at 10:50 AM
WyrTwister:I got what seems a very nice 200 amps Siemens circuit breaker panel about a year
ago: it comes with a copper ground rod, the buses are all copper, and it is really very large.
I don't have ...
Posted in thread: Telephone Wiring in Garage: What can I do with this? on 12-16-2015 at 08:20 AM
https://db.tt/2cF7tOnHi was just getting around to what the NID looked like and how it was
grounded.....so the grounding wire that comes from INSIDE the house goes to the grounding bar
in the NID so t...
Posted in thread: Weather Head to Socket Meter SER/SEU Cable Upgrade on 12-16-2015 at 08:11 AM
Best I remember , if you upgrade it to # 2 AWG copper , protection is not required ? I ,
personally would look it up in the NEC and do it that way , if the inspector had a problem with
it .God blessWy...
Posted in thread: Wire Routing Question on 12-16-2015 at 07:56 AM
Dining room has special requirements. The receptacles need to be on 20 amp circuits and the
circuit can't share with any other room except the kitchen.At the risk of being pedantic let me
point out th...
Posted in thread: to "derate" or not on 12-16-2015 at 07:46 AM
I'll be renovating one of my bathrooms. (don't know exactly when) I'd like to bring a 20a
circuit from the main panel to that bathroom since the GFCI is only 15a. (actually, every
"protected" outlet i...