Last Activity:09-06-2011 11:06 PM
Posted in thread: trane xl12 not cooling on 09-06-2011 at 11:06 PM
Thanks Paul for explaining how the system works. Now I understand why it was the run capacitor.
Posted in thread: trane xl12 not cooling on 09-02-2011 at 02:36 PM
yes it has it's own start capacitor, a run capacitor, and a capacitor switch relay. during
testing after being off for 2 hours the compressor would start the first time. then it would
cycle off and th...
Posted in thread: trane xl12 not cooling on 09-01-2011 at 01:46 AM
Hi, I have a Trane XL12 not cooling . yesterday the system froze up. Found the outside coil was
clogged with dirt . washed out the coils and restarted and system cooled house down to
68degrees and see...