Last Activity:06-03-2008 5:56 PM
Posted in thread: GFI Issue? on 06-04-2008 at 11:45 AM
the load side of the GFCI outlet went to a junction box. From the junction box one wire went to
1 outlet and another wire went to 3 outlets and the 2 wall sconces. The loose neutral was the
first of t...
Posted in thread: GFI Issue? on 06-03-2008 at 05:56 PM
thanks to all who provided input. I replaced the GFCI outlet and the same condition persisted.
I pulled the outlets and switch out one by one and checked the connections. Found a loose
neutral on, of ...
Posted in thread: GFI Issue? on 06-02-2008 at 07:53 AM
thanks all. i am going back to the RV today. I will check the existing outlets first for a
compromised neutral. I have a new GFCI outlet that I bought to replace the existing one if the
Posted in thread: GFI Issue? on 05-29-2008 at 07:10 AM
I have a circuit that has 3 outlets that work fine. Then there is a GFI Outlet which also works
fine. There are four outlets and two small wall sconce lights that do not work. Using a plug