Last Activity:05-26-2015 10:37 AM
Likes Given: 4
130 Likes on 106 Posts
Posted in thread: Big Pipe Mystery! What is this? on 05-24-2015 at 09:40 PM
Stick a pole or snake down it and see how deep it goes or if it takes a turn.It could have been
a mounting hole some other item.
Posted in thread: shower head tube to riser 90 cx on 05-18-2015 at 09:28 AM
There is not a lot of water pressure on the that joint, plus it only has water in it when
taking a shower.
Posted in thread: Voltage reduction? on 05-13-2015 at 08:58 PM
Depending on the issue there are underground rated splice kits available that might fix the
Posted in thread: Removing wall on 05-13-2015 at 01:25 PM
My non engineer thoughts.You can just remove the wall.The green struts are to hold the wall.
Remove the wall and now the struts are not needed.The 2x6 top plate is just a stiffener. Again
remove the w...
Posted in thread: Voltage reduction? on 05-12-2015 at 04:09 PM
1. Not code compliant. All the cables/wires must be in the same conduit or cable assembly.
Posted in thread: Voltage reduction? on 05-10-2015 at 06:34 PM
I'm a little rusty on my code on this, but because the workshop is a separate building, and
only 240 with a neutral are feeding it, then shouldn't the sub panel's neutral and grounding
blocks be bonde...
Posted in thread: Voltage reduction? on 05-09-2015 at 09:46 PM
Your 120 volt can't work with out neutral, something is hooked up somewhere.It can work but not
properly by feeding through the other hot. The loads are in series and if they are balanced you
Posted in thread: Voltage reduction? on 05-08-2015 at 01:46 PM
The neutral has to be in the same conduit or cable as the hot wires.If he replaces to the wires
save the old ones. They have value at the scrap dealer.
Posted in thread: Voltage reduction? on 05-01-2015 at 05:29 PM
The splice is not likely the problem. It is was it would be loose. It would also probably look
burnt or overheated.
Posted in thread: Voltage reduction? on 04-30-2015 at 08:31 PM
Splice looks fine. Tape it back up.