Last Activity:08-20-2009 11:02 PM
Posted in thread: Lennox compressor won't stay on on 08-19-2009 at 08:12 PM
Sounds like you are low on freon which would cause compressor to go "off" on low pressure
switch-pressure switch is located inside condensor. Check system charge.
Posted in thread: Freon copper in the wall and condensation pump in the attic on 08-19-2009 at 07:57 PM
Have the condensate pump wired in series with the control voltage-wired this way if the pump
fails the unit will not come "on" and you will know you have a problem- this will happen before
Posted in thread: York attic thru the wall a/c on 08-19-2009 at 07:33 PM
did not change blade for condensor-evaporator is a sqiurrel cage. this is the 2nd motor-(after
thinking i had elimated all other possibllities i came to the same conclusion). i am working
behind a ano...
Posted in thread: York attic thru the wall a/c on 08-19-2009 at 05:37 AM
double shaft motor-old unit
Posted in thread: York attic thru the wall a/c on 08-17-2009 at 02:55 PM
looking for some suggestions. unit has a double shafted motor whitch is going off on internal
thermal overload. this is a new manufactures suggested replacement motor. amps,rpm's, and
voltage are iden...