Last Activity:01-07-2008 7:50 AM
Posted in thread: Plasma TV Color Issues on 12-07-2007 at 09:38 PM
30 lashes for not getting a warranty, and 30 more lashes for buying a plasma, lol, you would
have been better off with an LCD.I am assuming you went into the setup menu and adjusted the
color and pict...
Posted in thread: Television safety question on 12-07-2007 at 09:28 PM
If you touch the television do you get a shock as well; or is it only when you touch the DVD
player? Also, is there another power outlet you can try? Maybe with an extension cord.
Posted in thread: Most everyone has one... on 12-07-2007 at 09:22 PM
Thanks for the tip. This is really a good idea. Isn't it amazing how the simplest things make
the most sense.Thanks again.
Posted in thread: Lennox A/C condensor fan motor on 11-30-2007 at 10:48 AM
-Lower the set point on the t'stat so the unit will call for cooling.-Measure the voltage on
the coil of the contactor to be sure you are getting 24VAC.-Then puch the contactor and release
it and see ...
Posted in thread: Lennox A/C condensor fan motor on 11-29-2007 at 11:43 AM
GWSIt may also be a good idea to verify the VA or load voltage rating on the transformer. If it
is too low, this could be the cause of your woes.
Posted in thread: Newbie Question Please help!!!! on 11-28-2007 at 10:33 AM
I believe those are the control wires. Just to be sure, engerize your system and check them
with a volt meter. This will tell you if they are the control wires and which is hot and which
Posted in thread: Thermostat issue on baseboard heater on 11-28-2007 at 07:19 AM
Glenn is correct. With that voltage you will need a double pole stat.Let me know how it worksk
Posted in thread: Thermostat issue on baseboard heater on 11-27-2007 at 11:30 AM
Is your thermostat and mechanical or electronic thermostat?If it is electroninc it requires a
ground or neutral.If you replaced both the heater and the stat I'm thinking that the problem is
Posted in thread: carrier central unit on 11-27-2007 at 10:47 AM
Did you check the contactor. The only way the fan will run is if the contactor is energized.
Something has to be keeping the contactor engaged. I would check the contactor to see if it is
pulled in. i...
Posted in thread: Wireless Thermostats on 11-12-2007 at 08:35 PM
Not a problem. No harm done.
- Floor Drain for AC Condensate Discharge
- Embedded Cleanout Covers
- Carrier HVAC - Fan not turning
- Can you tell me what it is called, please?
- Popping tiles
- Transistion problem
- Re attaching flagstone in walkway
- One Word Game
- What's that smell?
- Musky smelling rugs
- Builder's Joke Thread
- wiring thermostat
- Stucco Job
- Stainless Steel Fridge
- moisture from missing singles at roof peak?
- Shower pan