- Posts 27
Last Activity:06-17-2013 9:05 PM
Likes Given: 6
9 Likes on 7 Posts
Posted in thread: carrier model 50js--048--301 on 06-02-2013 at 08:58 PM
Take off the panel right above where your lineset connects on the unit. The capacitor should be
in there. Remember to kill the power before digging around in there. Have fun!
Posted in thread: New House, New Problems on 06-01-2013 at 09:11 PM
Shut the power off to your furnace. Get a volt meter and head outside to your a/c condensing
unit. Shut off the disconnect and gain access to the electrical. Remove the two wires going to
Posted in thread: No power to my thermostat on 05-31-2013 at 09:29 PM
Those darn condensate pumps and their safety features! Usually don't see this issue unless
furnace/air handler is installed in an attic or upstairs area. But good post about what could
be a possibly o...
Posted in thread: Opinion on service charge on 05-31-2013 at 09:21 PM
Thats sounds about right to me. As stated by kok328, the price of R22 has gone way up due to it
being phased out. The other option would be to take this oppurtunity to update your system to a
Posted in thread: Size of intake vent? on 05-18-2013 at 04:40 PM
I take it this isn't the only return air for the furnace? You need to have the same square
inches of return as you do of supply. So say you are bringing 2 6" runs into your bedroom, this
Posted in thread: Looking for new HVAC and move furnace? on 04-19-2013 at 05:42 PM
Oh and upgrade that dinosaur furnace to an energy efficient one while your spending the money.
It will be a lot quieter as :D
Posted in thread: Looking for new HVAC and move furnace? on 04-19-2013 at 05:39 PM
Centralizing in the attic is a viable option as long as it is installed correctly. Drip pan
under the entire unit with a drain, everything insulated properly, unit supported properly with
Posted in thread: Carrier furnace short cycling on 04-19-2013 at 05:25 PM
4 minutes is way too long between when the burners ignite and when the blower motor comes on.
Sounds like its shutting down on high limit, cooling down when the blower comes on, closing the
Posted in thread: Help with Trane Model 2TWB3030A1000A on 04-19-2013 at 05:12 PM
Anyway if that's the case it sounds like your reversing valve coil may have failed in the
winter heating months. If this is the case it usually fails open which would still allow it to
heat fine. Your...
Posted in thread: Help with Trane Model 2TWB3030A1000A on 04-19-2013 at 04:38 PM
So you are saying that the condenser fan will start up again after it comes to a stop if you
spin it manually? And that you changed the capacitor without testing it and it didnt help the