Last Activity:08-25-2008 12:24 PM
Posted in thread: Feeder to detached barn, Cable selection on 08-26-2008 at 08:00 PM
Thanks for the reply. It all sounds reasonable except I had a question on the 24" deep
statement. Is this just your preference for added safety or am I misreading the code? Table
300.5 in the NEC 2008...
Posted in thread: Feeder to detached barn, Cable selection on 08-24-2008 at 07:13 PM
I have a small house in the country with a metal barn about 50 ft. away. I want to run a feeder
from the main panel of the house to the barn. I plan to do the following:1. Come off a spare 30
- Floor Drain for AC Condensate Discharge
- Embedded Cleanout Covers
- Carrier HVAC - Fan not turning
- Can you tell me what it is called, please?
- Popping tiles
- Transistion problem
- Re attaching flagstone in walkway
- One Word Game
- What's that smell?
- Musky smelling rugs
- Builder's Joke Thread
- wiring thermostat
- Stucco Job
- Stainless Steel Fridge
- moisture from missing singles at roof peak?
- Shower pan