Last Activity:12-17-2014 5:18 PM
Likes Given: 65
116 Likes on 101 Posts
Posted in thread: Ignitor not coming on on 12-17-2014 at 05:17 PM
If I understand correctly the White Rodgers controller is the thermostat and you want to reset
that ?What is your model # for the controller ?Could have battery backup.
Posted in thread: Ignitor not coming on on 12-16-2014 at 05:35 PM
Reset the entire unit by turning off the service switch typically located on or near the
furnace.Removing and reinstalling the front panel achieves the same thing. Any LED on the
control board, flashi...
Posted in thread: Plaster Repair on 12-08-2014 at 05:52 PM
I've seen few threads on repairing plaster surfaces and have seen some plaster repair
materials/kits in the stores but, have never seen any explanation as to why you can't or
shouldn't repair plaster ...
Posted in thread: Lennox AC Compressor Problems -- Capacitor? on 12-06-2014 at 06:15 PM
Check for steady voltage on the contactor coil and if it I s good then replace the contactor.
Around $25. 24vac/30 amp 2-pole. About 30 minutes of work. Larger more expensive contactors can
Posted in thread: tiling info on 12-05-2014 at 12:15 PM
Flush to avoid having to install shims to eliminate wobble
Posted in thread: Befuddled over a fireplace! on 12-04-2014 at 05:36 PM
Is a steel plate an option for the base ?
Posted in thread: Securing Hose Bib on 12-03-2014 at 10:00 AM
I love the ingenuity of fixing the bad valve.I don't think that is a ground wire as it just
loops around the sill cock, it looks like a water meter wire or a phone wire.Frodo is correct,
when it comes...
Posted in thread: Gas Log Fireplace Advice Please on 11-29-2014 at 12:37 PM
Replace the thermocouple if that doesn't fix it then the gas valve is bad.
Posted in thread: Correct installation of black pipe for gas on 11-28-2014 at 12:13 PM
remove the cap from the trap, install a Tee fitting and then put a 4" pipe on one end of the
tee and attach you gas supply to the middle outlet of the tee. Basically, installing a tee to
provide a tie...
Posted in thread: Lennox headoffice contact? on 11-25-2014 at 07:51 AM
It would have to be wired into the fan circuit of the furnace so you can set the fan to "On"
versus "Auto" and would open the solenoid valve for the water supply when the fan is running.