- Posts 12
Last Activity:08-17-2010 4:55 PM
Posted in thread: help with 3 way wiring on 06-08-2010 at 03:55 PM
You are showing all 4 switches as 3 way switches , are all these switches controlling the same
lights? If so there has to be 2 4 way switches involved . You can not use 3 way switches in all
Posted in thread: Range wiring on 12-12-2009 at 04:07 PM
Nobody seems to understand what i am asking. I would like to find out how a #10 neutral got to
the range location. I know what the neutral does once it get there. What I am saying is they do
not make ...
Posted in thread: Range wiring on 12-12-2009 at 02:17 PM
I guess you did not understand what i was saying. Normally all the conductors in a cable are
the same size. they do not under size the neutral. So the question i am asking is how there is
only a #10 n...
Posted in thread: Range wiring on 12-12-2009 at 09:15 AM
The wire size is correct for a 50 amp circuit,#6 is rated for 60 amps,but what i do not
understand is you say the neutral is a #10. In a normal cable all the conductors are the same
size except for th...
Posted in thread: A pair of three-ways on 11-29-2009 at 12:55 PM
Joe Did you look a the drawing slownsteady posted on one of his threads. It clearly shows the
hot and the neutral in the same cable. They use the lighting box to do there make up. There is
nothing in ...
Posted in thread: A pair of three-ways on 11-27-2009 at 04:09 AM
Thanks for the drawing. That what i thought was happening but wasn't sure. It is odd but it
Posted in thread: A pair of three-ways on 11-26-2009 at 10:52 AM
can you id the switch legs going to then lights? Who ever wired the existing switches must not
of had any 14-3. if you had 3 14-2 in the switch box they had to be using 2 of the 14-2 as
travelers and ...
Posted in thread: A pair of three-ways on 11-26-2009 at 07:59 AM
Are these 3 way switch existing or are you wanting to make them 3 ways. if they are existing
did they work at one time? I am a little confused. Is there a 14-3 at both 3 way switch
location or is one ...
Posted in thread: A pair of three-ways on 11-25-2009 at 09:48 PM
if you have just 2 14-3 in the switch box most likely all the make up is done in the second
switch locations. The hot and the switch legs could both be in the second switch location and
that may be wh...
Posted in thread: 1890 house wiring issues. Help! on 11-03-2009 at 07:02 PM
Do you Know exactly what is on the circuit, and how far did the electrician trace it before he
gave up. It sound like you have circuit breaker so some of the electrical has already been
ungraded. Are ...