Last Activity:07-14-2009 5:08 PM
Posted in thread: no AC in July, what fun on 07-14-2009 at 03:49 PM
had an AC tech friend stop by, turned out to be delay relay on outside unitthe old mercury
switch therm required itwith the new therm it's built in, so he bypassed the outside delay,
Posted in thread: no AC in July, what fun on 07-14-2009 at 09:37 AM
Thanks Kok328, I'm a semi-literate fool when it comes to AC/electrical, the only stuff I've
learned is from trial&error and phone calls to friends of friends in the businessis the
transformer in the a...
Posted in thread: no AC in July, what fun on 07-14-2009 at 08:19 AM
when contactor manually pushed in, compressor seems to run OK, but contactor won't stay
drawn-in, fan runs constantly
Posted in thread: no AC in July, what fun on 07-14-2009 at 08:17 AM
couldn't find 24V anywhere, 18-19V at a few spots and 4-5V at otherstransformer?
Posted in thread: no AC in July, what fun on 07-13-2009 at 09:53 PM
it's a rheem heat pump, copeland scroll compressorhad an issue two weeks ago, seemed to be worn
contactor, replaced it, things seemed ok for a couple of daysnext replaced thermostat, old
- Exhaust Fan In Bathroom
- One Word Game
- Removing Felt Backed Linoleum
- Cast Iron Pipe Separation
- Best way to get rid of dandelions from the yard
- Aggressive Deer
- Excel Workbook
- Bad block foundation options
- Possible mold problems??
- Installing new garbage disposal
- question about water from central a/c
- deck roof and gutter question
- A little help with hardware, please?