- Posts 1
Last Activity:09-17-2012 5:32 AM
Posted in thread: bad transformer? on 09-16-2012 at 11:32 PM
If you have a 110v at the furnace then you have 110v into transformer, which is called the
primary, test the secondary side of transformer (24v) by followingthe leads from transformer
going to the low...