Last Activity:04-22-2009 8:59 AM
Posted in thread: York Stellar Plus won’t ignite on 11-17-2008 at 07:38 AM
Unit continues to work fine, tested by temps in the 20-s at night couple of times.York part #
for FLAME ROLLOUT switch pictured in post #12 is 025-26908-000 and I bought it real cheap
hereThank to kok...
Posted in thread: York Stellar Plus won’t ignite on 11-11-2008 at 10:07 AM
Works for now(fingers crossed).Turned out inducer blower was working, but not good enough to
close the pressure switch.Removed inducer blower, vacuumed inside, rotated fan manually.Removed
Posted in thread: York Stellar Plus won’t ignite on 11-09-2008 at 12:44 PM
Some history:At the end of last heating season this unit would ignite burners and after a short
while the flame would go out. I left it at that till new season, and when decided to take a
look – it wo...
Posted in thread: York Stellar Plus won’t ignite on 11-09-2008 at 08:07 AM
Yea, that would fall under the "got his heat working" catagorey. Lord knows, I wasn't getting
him anywhere.You helped a lot and it's much appreciated , especially as problem still stands.I
was just di...
Posted in thread: York Stellar Plus won’t ignite on 11-04-2008 at 03:50 PM
the switch/fuse has no continuity, needs to be replaced.I searched for exact same one, found
info but no place to buy it.It opens at 152 degrees C or 306 F.I think it was not supposed to
be there. Is ...
Posted in thread: York Stellar Plus won’t ignite on 11-04-2008 at 08:16 AM
You were right on!The switch! First I didn’t see anything in the burn chamber, then
looked in our main unit York Diamond 80 and saw the cylinder switch! In this small broken unit
same wires just...
Posted in thread: York Stellar Plus won’t ignite on 11-03-2008 at 12:18 PM
sure feels like something stupid (disconnected wire), before the pressure switches.Found
troubleshotting manual for control board through chart 1(page 2)with inducer running there is
25v between C an...
Posted in thread: York Stellar Plus won’t ignite on 11-02-2008 at 08:25 AM
There is what I suspect is a limit switch, round with 3 tabs, has too many wires connected, how
to check it ?Checked pipes – clean.This unit is heating/cooling and cooling is fine, I
had to say ...
Posted in thread: York Stellar Plus won’t ignite on 11-01-2008 at 03:31 PM
Gas is on; blue switch inside and red outside. Pressure switches not connected with each
other.LEFT one(with 3 wires) connected by tube to inducer motor. Tube from the RIGHT
switch(with 2 wires) split...
Posted in thread: York Stellar Plus won’t ignite on 11-01-2008 at 08:55 AM
Ignator looks like this electronic means no pilot light, then it's electronic.Normally it
should glow, but does nothing.Somethere I read(not about my model), that there should be 115 v
coming to igna...
- Small cabin help..?
- Basement Plumbing and Flooding Questions
- Your house is how old?
- Paint Chiping in Bathtub
- Driveway Sealer
- drylocking basement and removing mold on concrete
- Bathroom tiling
- Flooding Driveway
- One Word Game
- Completed Sanding, two questions before applying urethane finish.
- Install Quarter Round when there is large gap underneath the baseboard?
- Sistering floor joists in my hunting cabin to stop floor movement
- Shower pan
- Need opinions on what to do here... (Pics Included)
- Possible mold problems??
- Need some help