Last Activity:05-09-2008 4:55 PM
Posted in thread: Condenser fan won't shut off on 05-18-2008 at 04:21 PM
Thought I'd give a quick reply so maybe I can help someone in the future with this issue.I had
a "pro" come out and look. The compressor blew out one of its three contacts and current is
feeding back ...
Posted in thread: Condenser fan won't shut off on 05-09-2008 at 03:54 PM
Connect the fan motor to the same side of the contactor as the compressor leads. It is. My DVM
reads ~130 volts across the output of the contactor while the one leg of the contactor is open
Posted in thread: Condenser fan won't shut off on 05-08-2008 at 08:00 PM
I don't have much experience in HVAC, but it seems like a very basic system. It's a Bryant unit
using a Copeland scroll compressor.The outside unit seems very simple. The only electrical
Posted in thread: Condenser fan won't shut off on 05-08-2008 at 05:44 PM
This is a strange problem with my home AC...my condenser fan will not stop unless I kill the
power to the unit. I have replaced all of the components (contactor, capacitors, and even the
fan motor) in...