DIY Home Improvement, Remodeling & Repair Forum > Cathedral ceiling - how much venting do I need?

10-22-2012, 03:11 PM
Shawner
Member

Join Date: Oct 2009
Location: Peachland, BC
Posts: 56
Liked 2 Times on 2 Posts
Likes Given: 4

Cathedral ceiling - how much venting do I need?

Guys, meet my roof. Well, part of it anyways. The raised part is the cathedral section.

Here's the exhaust side of the venting. Aluminum soffits are covering up cedar with holes drilled into it. Haven't pulled them down yet to see exactly how much there is.

Found a site about calculating proper attic ventilation (http://www.trinityexteriorsinc.com/1...n-5-easy-steps), wondering if you could check my calcs below and see if I'm correct.

Area = 25' x 23' = 575 sq ft

TFNVA = 575 sq ft / 150 = 3.83 sq ft

Convert to inches = 3.83 sq ft * 144 = 552 sq in

Intake = 60% = 331 sq in
Exhaust = 40% = 221 sq in

So if I pull down the soffits, count the number of joist bays I have, figure out the size of hole I need to cut in each to total 331 sq in on the intake side, I should be good, right? If that's ok, should I staple in some screen material over the holes to keep the critters out or do the soffits do that already?

I'm not positive but I don't think I have to worry about baffles (don't think the insulation is up that high in the "attic")

Thanks for any help!

__________________

10-22-2012, 03:37 PM
nealtw
Contractor

Join Date: Nov 2010
Location: Upper Fraser Valley, British Columbia
Posts: 12,559
Liked 1222 Times on 1077 Posts
Likes Given: 2042

If the white soffet was part of the original construction the cedar would not be there. If you are taking it down to drill more holes, I would just remove one peice of cedar all the way across
The lower roof is vented below the windows with 3 holes for bay, I think I would want more there and maybe better protection for that venting.

__________________

10-22-2012, 03:51 PM
Shawner
Member

Join Date: Oct 2009
Location: Peachland, BC
Posts: 56
Liked 2 Times on 2 Posts
Likes Given: 4

Don't think the aluminum was original. Think it used to have cedar shake roof, they probably put the soffits on when they sheeted the roof and put asphalt shingles on.

Good plan on removing one chunk, lot easier than cutting lots of holes.

__________________

10-22-2012, 04:13 PM
nealtw
Contractor

Join Date: Nov 2010
Location: Upper Fraser Valley, British Columbia
Posts: 12,559
Liked 1222 Times on 1077 Posts
Likes Given: 2042

I would take a close look at the lower one too. Those little hole give you min. venting at best but the top board looks level so you may have water sitting way to close to those windows. I'm sure something better could be done.

__________________

10-22-2012, 05:30 PM
oldognewtrick
Moderator

Join Date: Jul 2009
Location: Nashville, TN
Posts: 6,630
Liked 625 Times on 515 Posts
Likes Given: 198

There is a exhaust vent that is applied from above. It's like half of a shingle over ridge vent, then you put a metal "L" flashing over the top of it. One brand is called Smart vent.

http://www.dciproducts.com/html/smartvent.htm

__________________

10-22-2012, 05:36 PM
AndyGump
Drawer of Homes

Join Date: Mar 2011
Location: Orange, CA.
Posts: 56
Liked 5 Times on 3 Posts
Likes Given: 2

I think you would be better off making the high end (exhaust) the 60%.

If fact, I know it would be.

Andy.

__________________

10-22-2012, 06:20 PM
nealtw
Contractor

Join Date: Nov 2010
Location: Upper Fraser Valley, British Columbia
Posts: 12,559
Liked 1222 Times on 1077 Posts
Likes Given: 2042

Andy: You lost me, a little more detail?

__________________

10-22-2012, 07:16 PM
Wuzzat?
Banned

Join Date: Jan 2010
Posts: 2,328
Liked 168 Times on 155 Posts
Likes Given: 94

Quote:
 Originally Posted by Shawner Intake = 60% = 331 sq in
sqrt(331) = ~18" on a side for a square vent. You may want to make two vents that add to this area.

I'd redo for the 300 ratio just to see what kind of latitude you have on these dims.

Quote:
 Originally Posted by AndyGump I think you would be better off making the high end (exhaust) the 60%. Andy.
If you're thinking stack effect that may already be in the 60/40 split.
__________________

Last edited by Wuzzat?; 10-22-2012 at 07:21 PM.

10-22-2012, 07:49 PM
AndyGump
Drawer of Homes

Join Date: Mar 2011
Location: Orange, CA.
Posts: 56
Liked 5 Times on 3 Posts
Likes Given: 2

Quote:
 Intake = 60% = 331 sq in Exhaust = 40% = 221 sq in
This is what he stated.

Should reverse those percentages.

Andy.
__________________

10-23-2012, 04:36 AM
oldognewtrick
Moderator

Join Date: Jul 2009
Location: Nashville, TN
Posts: 6,630
Liked 625 Times on 515 Posts
Likes Given: 198

First thing to check is the ability to free flow air from the eave to the peak, because if it's stuffed with insulation all the venting in the world will not help.

__________________

nealtw Likes This