the desired Kitchen exhaust ventilation is approx a minimum 12 air changes per hour(ACH) this is achieved by installing an exhaust hood FAN that is capable of exhausting the entire cubic feet of your Kitchen 12 times in a hour. The fan is rated in cubic feet per minute (CFM)
Eg; a kitchen 12' x12' and with 8' high walls = 1152 cubic feet (1200 cu ft.)
a fan sized at 240 cfm would exhaust this 1200 cu ft in 5 minutes,or 1 complete air change.
if it ran for the entire 60 minutes it would completely change the air in the kitchen 12 times.
What size is your kitchen?
Note; some pros suggest the air changes in a kitchen should be even as high as 15 air changes in a hour(ach)
A lot depends on the kichens layout,etc.
Please consider this; there has to be air comming in from somewhere in order to exhaust that much air. You said it is a new house, which is normally tightly sealed, I would suggest an 8" make-up air duct to feed the exhaust fan. The make-up air duct can be dampered and regulated to limit the rush of cold air and there are heat exchangers on the market to economize on the lost heat. Or, you could run the make-up air into the return air duct to come through the heating system which would call for a considerable up-sizing of the heating system. Just some thoughts that go along with exhaust air.
Buy one with a Hemi on it LJ!
You'll hear a certain wooshing sound around all of your windows and doors, but your cat will be gone for good.
Use the throttle for a damper.
Will displace all of the air in your house in less than a second
Use round metal duct with an internal damper (a round piece of metal that is almost as big as the duct, with an external handle on it). No, a fan is not necessary for the make-up. AprilAire.com makes an air exchange unit called PerfectAire; its worth checking out.
The average built home of to-day would still provide enough infiltration to provide sufficient air flow for the average kitchen exhaust fan.
An exhaust fan run for a short time to exhaust kitchen odors, etc would create no problem.
However, if you are planning to run this fan several hours in a day, yes without make- up air there could be a "negative " pressure created within the home.
One way to prevent this negativity to happen would be to install a HRV or ERV system which will bring in fresh air and expel any stale and moist air. This type of system can be set up with an air measuring instrument (magnehelic) and also will reclaim most of the heat from any stale air that is expelled and this heat can be put back into the home . This is especially efficient for those cold winter months.
Another inexpensive way to provide "make-up air" (if it's needed) is to install a "ventamatic damper". It has a screened intake with a flapper that only opens when it is "drawn" open by the operation of the kitchen fan.It is gravity operated, no electric power needed.this type of damper can be placed anywhere within the home.