The 2 hots are each 120 volts
You can share the neutral if you keep a double pole (240v) breaker in the main panel.
If you plan on using a sub-panel at the deck, you can keep the 50 amp breaker you have now in the main panel, then use 20 amp single pole breakers in the sub-panel. Then you'll have 4 110 volt circuits.
[URL="http://www.houserepairtalk.com/announcement.php?f=39&a=6"][size=3]The Ten Commandments of House Repair Talk[/size][/URL]
[URL="http://home.bellsouth.net/p/s/community.dll?ep=16&groupid=289528&ck="]Square Eye's home page[/URL]