That will NOT work. You need to run the hot and the neautral together. Either run both of them through the GFI or none of them. Otherwise, it will trip the GFI with hot skiping the GFI.
Also, You want to ground the light and fan as well. Also, this means the line and fan will be GFI protected. Do you want that?
Master Electrician, Air Conditioning & Heating Repair Company Owner. www.TECertifiedElectricians.com
Last edited by ohmy; 01-14-2010 at 04:10 PM.