I know this post is over two years old, but it makes me ask your opinion on this. I have run a 12-3 to a box and split to two seperate gfi plugs. And just tailed all my neutrals together before hooking to line side of plug. I thought they only had a problem if you touch the neutrals on load side. Is this correct? or should I look forward to some phone calls?