Based onthe depth and direction I would guess a floor drain possibly.
Hot neutral reverse will not stop MW from working. I think it was just a coincidence that it started working after you swapped them. Maybe one of...
I agree. Main water shut off. Call the town water department.
You don't have keep updating but if you make changes you have to meet current code.
Current code, unless you have a local amendment, requires all receptacles, including in the ceiling, to be GFCI protected.
Bolt cutter would be my choice. It will cut the ties to the poles and the fence wires.
Fence is too floppy for a saw. It would just fling back and...
All receptacles in the garage must be GFCI protected.
Yes there would be an always hot at one switch. However there might not be a neutral at either switch.
Pig tail a short piece of #14 or #12 to match the breaker.
How long do you think it will take per pole? Are you paying for the paint and charging them? What do you think your time is worth?
Are more than one circuit affected? It sounds to me like one of the hot wires feeding your house has a loose connection. Turning on the AC back...
This thread is 5 years old.
I have not seen those before but I am certain that loosens from the top.
If you had a double pole thermostat you would never have known. Good find.
The pump must have some sort of auto shut off that detects running too long and shuts the pump down. Flipping the breaker reset it. Normally the...
Unless you are broke and can't afford it, I would pay it.
If it breaks your budget consider doing the painting your self.
Could you have a the barn boards planed thinner. If you only plane one side it won't affect the look.
I would switch to a different type of box that allows the proper mounting. There is no reason to use box extenders when you know the proper depth...
The only to be sure where the property line is located is a survey.
Dehumidifier and insulate the pipe to keep the moist air away from it.
Separate names with a comma.