With the summer heat we have noticed our 2nd floor isn't cooling off. I took a look in our attic and noticed the exhaust fan isnt running. Opened the junction box and noticed one of its white wire was disconnected. The Black wire is connected. Testing the power the only live wire is red. I do see two sets of white wires.