Tom, just want to be clear here. There is a meter with 200 amp breaker and ground rod. Then there are 3 wires to house with square d 200 amp breaker with it's own ground rod connected to neutral bar. So, this inside 1st panel is apparently not bonded but should? If the bond screw on that panel is top right on neutral bar it isn't there. I tried a ground screw from smaller box and it appears to be short. It would go in the smaller box but don't think in the 200 amp box. It is, I believe S series Square D QO box? ThanksYes that is correct.