Mike is this updated NEC Code saying that handrails that you do not have to bond your hand rails and ladders if the metal part does not exceed 4 inches?
Mine is only about 2 inches or 2 1/2 inches but they are bonded.
Thanks for advice. Now I see the difference in bonding and grounding. If you don't have to have a copper rod in the ground and the bonded equipment hooked to it, then I don't see why they did that in my pool 30 some odd years ago. Guess at that time either the code was different or they did not know the code.
This just gives me a place to connect everything to.
Does it hurt anything that the motors, heater and bonding system is connected to this coppy or brass rod?