I understood that ground wires do not have to be insulated and
I could not find anything prohibiting running ground wires from the new receptacle under quarter round, baseboards, or wherever, down to where you can find the metal inlet cold water pipe.
Does anyone have a code cite that could be interpreted in such a way as to contradict this? "Speak now, or . . ."