Hunter tstat with 2 wires - continuous fan won't turn on
I have a new goodman furnace installed in the winter and now that it is 35C outside I would like to have the blower fan on continuously to circulate air, but it won't turn on with the thermostat set to always on, not auto. The fan comes on when the heat comes on, but not without the heat on. It is a 2 wire system, and the tstat is jumpered from rc-rh .. Not sure what is wrong, but the furnace we had before worked in this way.
it is a hunter 47110a thermostat.