You're on the right track. Go to the store and get a cord, it may be a 12 or 14. Cut off the female end and voila, you have an appliance cord! There are tons of applications where myself and all the electricians have hooked up hardwire ovens that have a 10ga wire coming out of them, and they are on a 40amp breaker. The circuit might be 15 or 20 amps, but the d.w. only draws 8 or 9amps. Keep it simple, good luck.....
[COLOR="DarkGreen"][FONT="Franklin Gothic Medium"]See my work-Check out my album. "Git 'Er Done":D [/FONT][/COLOR]
Last edited by triple D; 04-30-2008 at 11:05 AM.