Is 20 Amp breaker too big for a fluorescent light
Built a basement closet which contains my (2) FPE 200 amp service boxes. I just mounted a T8 Two strip fluorescent light on the ceiling controlled by a single pole switch. All wires are ran...
I have a leftover 20 Amp breaker available (American Single pole HARC type), is this too big for this single light circuit? I have numerous open slots for new circuits.
If so, I don't want to buy a 15 Amp breaker due to big $$'s, so should I just tap into an existing 15 Amp circuit?
Thanks for your responses,