Discussion in 'Electrical and Wiring' started by rowdy48, Feb 1, 2012.
Anyone have the latest NEC requirement for access clearance around the panel ?
30 inches wide, 36 inches deep in front and 6 foot 7 inches high. The panel does not need to be in the center of the 30 inches. It can be to either edge or anywhere in between.
Thank you for the info
Separate names with a comma.