I have a single switch on the wall that controls a receptacle. I replaced the receptacle and switch and now the switch does not work. Both of the outlets on the receptacle work. I checked them and they are set up correct. If you are looking at the exterior of the outlet, the red wire is on the top right and the black is on the bottom right. One white wire is on the top left and the other is on the bottom left. I have tried all combinations with a single pole switch and 3 way switch. Does anyone have some information on what I must be missing or how I have it set up wrong?? That would be a big help since I am not frustrated at usually such an easy fix.